I have actually a switch the controls a light as watched in this diagram. There is no neutral at the switch, instead, it picks the up from what else. In the light receptacle that pigtails right into the light and also continues to the garage.
You are watching: No voltage hot to neutral but 120v hot to ground
I measure 120v in between the source hot and also ground, and also 120v once the switch is on in between the hot lead and also ground. In the light box, with the light disconnected I gain 19v from neutral come ground. With or there is no the light, I gain 90v in between the warm to neutral.
In the garage, the outlets read out 120v and also everything connected to them it seems ~ fine (work).
What is the right way to diagnose this? any kind of ideas why I"d be gaining 20v in the neutral?
boost this concern
edited Nov 4 "16 in ~ 21:36
asked Nov 4 "16 in ~ 21:16
14311 silver- badge77 bronze badges
include a comment |
1 answer 1
energetic oldest Votes
Basically the neutral has current trying to return earlier the the transformer and is dropping voltage as result of how a neutral is simply a collection circuit.
When the source hot passes thru the irradiate (as a parallel circuit), it proceeds out the neutral there is no dropping voltage.
The trouble with this circuit is the neutral and hot carry out not originate in the very same junction box and also is very confusing not just beer-selection.com"s but likewise electricians, no to mention a code violation.
boost this answer
edited Nov 4 "16 at 21:49
answer Nov 4 "16 in ~ 21:43
4,66522 gold badges1010 silver- badges3131 bronze title
add a comment |
Thanks for contributing response to Home development Stack Exchange!Please be sure to answer the question. Administer details and share your research!
But avoid …Asking because that help, clarification, or responding to other answers.Making statements based upon opinion; ago them up with recommendations or personal experience.
To learn more, watch our tips on writing an excellent answers.
See more: Ch A Hole Through A Bone Is Called A Natomy And Physiology: The Parts Of A Bone
Sign up or log in in
authorize up utilizing Google
sign up utilizing Facebook
authorize up utilizing Email and also Password
Post together a guest
email Required, but never shown
Post together a guest
Required, however never shown
post Your price Discard
Not the price you're looking for? Browse other questions tagged electric or ask your own question.
Featured top top Meta
Why is mine 3-prong dryer outlet mirroring 240V between hot and neutral/ground 'L' prong?
check ground present
60V warm to onward neutral
Neutral wires or neutral and also ground cause tiny “sparks”
open neutral bedroom outlets
Voltage native Neutral to Ground
120V on hot and neutral wires… simply started happening
Voltage in between neutral and also ground in receptacle
how do I determine why every outlets on a breaker stopped working, yet the hot-grounds are still 120V?
hot Network inquiries much more hot inquiries
i ordered it to RSS
inquiry feed To subscribe to this RSS feed, copy and also paste this URL right into your RSS reader.
stack Exchange Network
site architecture / logo design © 2021 ridge Exchange Inc; user contributions licensed under cc by-sa. Rev2021.9.17.40233